Electrical load diversity factor is a ratio representing the sum of the individual maximum demands for each part or parts of the system to the maximum demand of the entire system or parts of the system. Another factor that designers consider is demand factor.Know More
Demand factor is a ratio of the sums of maximum demand on a system to the total load on the system. Sometimes designers confuse the terms "demand factor" and "diversity factor."
In electrical design, diversity factor can be described by considering two buildings which have the same maximum demand but the demand is needed at different intervals of time. When the power is supplied by the same feeder, the demand is less than the sum of the two demands. Diversity factors have been designed for main feeders that supply power to multiple feeders which are typically 1.10 to 1.50 for lighting and 1.50 to 2.00 for power and lighting.
As an example, one can think of a feeder that supplies five users with the following load conditions: On Monday, the first person reached a maximum demand of 100 amps; on Tuesday the second user needs 95 amps; on Wednesday user three uses 85 amps; on Thursday user four needs 75 amps; and on Friday user five uses 65 amps. The feeders max demand is 250 amps. The diversity factor would be the sum of the demands divided by the maximum demand of the feeder and then multiplied by 100. In this instance 420 amps divided by 250 is 1.68 which when multiplied by 100 makes it 168%Learn more about Electricity
The ratio of cement by volume for standard concrete is one part Portland cement, three parts aggregate and three parts sand. General purpose mortar requires one part Portland cement, one part hydrated lime and three parts sand.Full Answer >
The ingredients in saline solution are non-iodized salt and boiled or distilled water, typically at a ratio of approximately 1 part salt to 100 parts water. A nasal saline solution includes baking soda in the ingredients.Full Answer >
The standard ratio for general purpose mortar, type N mortar, is one part Portland cement, one part lime and six parts sand. Type N mortar is typically used for exterior walls above ground level that are exposed to the elements. It is also appropriate for interior load-bearing walls.Full Answer >
An inductive load pulls a large amount of current when first energized, then settles down to a full-load running current after a few seconds or cycles. When switched, inductive loads can cause excessive voltages. Some examples of inductive loads include transformers, motors and wound control gear.Full Answer >