Video Results from YouTube.com
Published in : 2013-07-17 | by steven lavimoniere
AIR CONDITIONING: trane condenser over charged .head pressure was so high it was out on thermo overload when i got there ,i had to get the garden hose out ...
Published in : 2013-07-27 | by steven lavimoniere
AIR CONDITIONING :installed new split system in home ruun 1 1/2 ton.
Published in : 2015-07-06 | by steven lavimoniere
blocked condensate line backing water up into pan.
Published in : 2013-05-03 | by steven lavimoniere
AIR CONDITIONING: here i find a bad thermostat t87f sub base on a ruud split system........